Cables used as power and signalling cables in buildings with a large concentration of people, assets with increased requirements for fire safety and low fumes and corrosive gases during combustion e.g. in power plants, transformer stations, tunnels, hotels, airports, railway stations, subway stations, hospitals, banks, theatres, shopping centres, cinemas and multi-storey buildings, etc. Construction of core: cores of class 1 or 2 round. Operating temperature: up to +90°C, minimum ambient temperature for cables placed permanently: -30°C, minimum ambient temperature when placing a cable: -5°C, maximum temperature of a core during short circuit: +250°C.
FlameBlocker N2XH (0.6/1kV) DIN VDE 0276-604 and DIN VDE 0276-627 RoHS Directive 2002/95/WE, Low voltage Directive 2006/95/WE
FlameBlocker N2XCH (0.6/1kV) DIN VDE 0276-604 i DIN VDE 0276-627 RoHS Directive 2002/95/WE, Low voltage Directive 2006/95/WE
Flame spreading: DIN EN 50266-2-4 VDE 0482-266-2-4 IEC 60332-3-24
Emission of fumes: DIN EN 61034-2 VDE 0482-1034-2 IEC 61034-2
Gases corrosiveness: DIN EN 50267-2-2, VDE 0482-267-2-2, IEC 60754-2, pH≥4.3, conductivity ≤2.5µS/mm
Cables intended for the European market are classified in accordance with the requirements of the CPR directive.